Loosen as well as remove the screws from the cover for the light change that operates the light, utilizing a screwdriver. Take off the cover, and notice the colour of the cable insulating material for the cables that connect to every side of the switch. You’ll see white cables at one side of the change and black cables attached in the other side. Among the white and black wires goes to the luminaire. Another white and black cables are the electrical circuit for the switch. In case the light may be turned on or away from switches at every side of the room, you will see a blue cable which connects the electrical circuits for 3 way switches.
In several cases, it may run throughout the electric box where the present light is installed, but it is only even a change cable rather than a cable for the light. Look at the cables on the rear of the new luminaire, and notice black insulating material on one as well as white on the other. These connect to the corresponding white and black electrical wires that pass from the switch to the electric box where the present fixture is installed. There’s a bare copper ground cable that links to even a green grounding screw inside the electric box. Open the opening of wire nuts and mounting screws that came with the new luminaire. Whilst the light only has a white and black electrical cable, some producer include an addition wire nut since these are simple to lose when installing a light. In many cases, the nuts are the same colour, like red, yellow or black. Again, this depends upon the manufacturer, and any colour wire nut may be utilized to connect a corresponding colour of electrical and luminaire wires.